- Rain Penetration Class: D up to 3.5m/s
- Airflow Class: 1 (entry & discharge)
- Airflow Coefficient Ce (entry): 0.440
- Airflow Coefficient Cd (discharge): 0.434
- K factor (entry / discharge): 6.250 / 5.309
|Core Ventilation Rate (m/s)||0,0||0,5||1,0||1,5||2,0||2,5||3,0||3,5|
|Penetration Class (13m/s & 75mm/hr)||D||D||D||D||D||D||D||D|
|Airflow||Coefficient of Entry Ce||0,400||Class 1||Coefficient of Discharge Cd||0,434||Class 1|
RESISTANCE TO AIRFLOW – ENTRY (Ce)2
RESISTANCE TO AIRFLOW – DISCHARGE (Cd)2
Note: Based on a 1m x 1m size. Smaller louvres may have a higher Pressure Drop.
- Aluminium alloy 6063-T6
- Mill finish
- Clear or colour anodised
- Polyester powder coated Matt (standard) or gloss
The principal reason for using louvres is to allow the movement of air. But, louvre specification is a balance between form and function, with louvred façade appearance playing an important part in the selection process.